I recognise i need to replace the burden middle in my storage with a new, grounded unit. Don't forget, i'm rewiring a whole, extensive old house built in 1878, so getting the lights back on is first precedence - i will get to the garage whilst the residence is performed. The storage is powered with the aid of an underground 10-3 romex cable related to a 2 pole 30 amp breaker in my cutting-edge 200 amp major service panel in my basement. It is going to an vintage qo provider panel in the garage that has no principal breaker and no floor bar. There may be also a 12-three romex cable going to the storage to make the three way switches between the 2 buildings characteristic. Neither cable has a ground twine. Both cables are buried underneath my blacktop driveway and now not in conduit, so they're so difficult to replace that let's simply assume it's impossible.