Good Honeywell T6360 Room Thermostat Wiring Diagram Wiring Diagram For Honeywell Wall Thermostat Archives - A beep test will teach you a lot, keep the beep tester between terminals 1 and 3 and turn the dial if the beep doesnt switch then the stat is goosed however if this is a new stat then i might say its particularly unlikely and i would be surprised, its no longer not possible even though because it does appearance successfully stressed out, it could be possible the schematic is inaccurate and its honestly terminal four you need and no longer terminal three. Failing that its stressed out up effectively and is one of the fuses or connections in plug, socket connections, socket now not switched on , heater has transfer? Blah blah blah without voltmeter haven't any manner of operating it out over tinternet.
Check in now to advantage get entry to to all of our capabilities. Once registered and logged in, you may be capable of make contributions to this website by filing your own content material or replying to current content material. You will be capable of customize your profile, get hold of popularity points as a praise for submitting content, while also speaking with different individuals via your very own personal inbox, plus plenty extra!. When you have nominal voltage (230 ish) and 0v result between impartial and earth the plug is efficaciously stressed and fuse is functioning (any other way to check fuse is continuity check as before among the two ends of the fuse and if it beeps like before u have continuity and is great).
Was hoping someone within the realize may want to provide me a bit of advice on wiring up a honeywell t6360 to turn my oil rad on while temps drop underneath 22 celsius. I have searched on right here and wired it up how i thought became correct consistent with the wiring diagram and bits on here however it ain't working. Looks like you've got the mains stay and the heater live the wrong way spherical, if i consider proper from doing boilers the number 1 terminal turned into live in and 3 was the boiler aspect so three have to be heater, hope this helps.